The power cable is flat, with insulated copper conductors in a protective sheath of PVC compound.
CONDUCTOR ACCORDING TO GOST 22483
1. Copper, single-wire, round-shaped, Class 1. Number of conductors: 2-3, cross-section: 1.5-10 sq. mm
INSULATION AND SHEATH
Insulation and sheath of polyvinyl chloride compound.
Insulation of polyvinyl chloride compound; ОSheath of low-combustible polyvinyl chloride compound..
Insulation and sheath of polyvinyl chloride compound with low fire danger and reduced smoke and gas emission
Insulation and sheath of polyvinyl chloride compound with low fire danger, reduced smoke and gas emission and low toxicity of combustion products
The cables are designed for transmission and distribution of electric power in stationary electrical installations with a rated alternating voltage of 0.66 and 1 kV of a rated frequency of 50Hz.
The cables are designed for laying single cable lines in cable structures and premises. When laying such cables in groups, the use of fire protection means is mandatory.
Cables with the -ng(A) index are designed for group laying in cable structures of outdoor (open) electrical installations (overhead cable tray systems, cableways).
Cables with the -ng(A)-LS index are designed for group laying of cable lines in cable structures and premises of indoor (closed) electrical installations, including at nuclear power facilities. For electrical wiring in residential and public buildings.
Cables with the -ng(A)-LSLTx index are designed for use in cable structures and premises, including residential and public buildings, buildings of preschool educational institutions, specialized homes for elderly and disabled people, hospitals, dormitories of educational institutions, hotels, student residence buildings, sanatoriums and recreation centers, campsites, boarding houses, as well as for entertainment, club, sports facilities, buildings of public service organizations, subways.